1、 Installation method of cold storage board1. Floor in […]
1、 Installation method of cold storage board
1. Floor installation
1.1 first level the floor, then start to install the floor, select the beautiful floor and put it in a conspicuous place, and make the floor and evaporator drainage system.
1.2 quality requirements
The floor shall be installed flat, and the uneven part shall be padded with materials, and the hook between the locking plate and the plate shall be locked, so as to achieve the flatness of the warehouse surface without hollow feeling. (note that if the drainage system is installed in the North outdoor, the drainage pipe needs to be insulated).
2. Vertical plate installation
2.1 select a corner first according to the site conditions, and locate (i.e. the vertical plate is locked with the floor) to extend to both sides with this corner, only lock the vertical plate and the vertical plate, and locate when meeting the vertical corner. The beautiful plate is placed in a conspicuous place. When it is installed on the evaporator side, the drainage pipe shall be done in advance, and U-bend and silica gel shall be made outside the warehouse.
2.2 the conspicuous surface of the vertical plate shall be flat, the storehouse plate shall have no concave points, the top surface of the vertical plate shall be flush, the gap between the vertical plate and the vertical plate shall be even, and the vertical angle of the conspicuous part shall be flush with the floor angle.
3. Installation of ceiling
3.1 first select one end to locate the crown angle plate and extend the laying, lock the crown plate and the crown plate, and during the installation, the crown plate and the vertical plate are conspicuously locked to ensure the flatness, so as to prevent running.
3.2 beautiful ceiling shall be selected for the prominent part, and the joints between the ceiling and the vertical slab shall be flush, with small gaps, and the space between the ceiling in the warehouse shall be flat.
4. After the sky, ground and vertical plates are generally installed, they shall be corrected, leveled and locked, and all hooks shall be locked with each other.
5. When encountering the warehouse plate to be flared, the flared part shall be polished without burr. When encountering the warehouse plate to be angled aluminum, silica gel and then angled aluminum shall be pulled to ensure the tightness.
6. After the warehouse body is installed, the silica gel shall be applied at the time of arrangement, and the silica gel joint shall be smooth and smooth. The silica gel shall be applied at the end of the day to avoid damage.